Project Scope for:
Power for Security Trailer, Truck Heater Receptacles and Pole Lighting.
Underground locator service completed and
High voltage conduit ran to the new Transformer Pad.
8 inches of crush stone as per specifications for
Lighting discoveries begun. Looking for best case
LED Flood Light with similar mounting bracket.
175 Watt LED
approx. 700 watt equal.
The white lines indicate the plans for excavation.
41 Feet from the
HV Termination Pit
(red painted 2X4) to the new Transformer Pad.
The PECO Transformer to be located here.
This location is inside the property line approx 75FT back from the street.
New 7' X 7'
Precast Transformer Pad to be placed here.
Secondary from this point to the new Security Trailer approx 56 Feet
Location of the new Security Trailer.
Electrical service to be located 18 Feet from the fence in the rear (center of
first parking space orange paint).
New Electrical Service to be
installed here on concrete mounted pole/strut supports.
-Control Box for Exterior Lighting.
Truck Heater Receptacles to be located
here along the fence.
Receptacles to be concrete mounted uni-strut approx 1.5 Feet away from the fence
and center of parking spaces 4. 5. 6. 7.
Lighting Circuit conduit to be brought up to the first light pole (approx 80FT).
Underground cable inspections made.
Circuit tracing and underground conduit locating required.
This is the
"Point of Origin" of underground circuits to the existing pole lights.
These cables must be diverted to inside the property line of the customer.
80FT from Service to
First Parking Lot Pole.
60FT from Service to
Truck Heater #4.
18FT from Service to Fence.
38FT from Transformer to
41FT. from HV Terminal Pit to the new XFMR